Exele OPC Products and Hardening DCOM Changes (KB5004442)
Due to a vulnerability detailed in CVE-2021-26414, Microsoft released a security update in June 2021 which will change the level of DCOM security required between OPC Classic clients and remote OPC servers. Once implemented, this change will cause connection failures between many OPC clients and remote OPC servers including Exele OPC client products TopView OPC/SCADA, TopView OPC A&E, and OPCcalc.
Which OPC clients will not be affected by this change?
The following OPC Classic clients/servers are not affected by this change:
- OPC clients and servers on the same machine
- OPC clients that implement Packet Integrity authentication level
- Remote OPC clients and servers that use an OPC tunneller if the tunneller makes local OPC connections on both machines
How are Exele OPC client products affected by this change?
Our current release of OPC client products (as of December 2021) do not implement the required client security level “Packet Integrity”. We have created a patch to address this issue.
Patching will be available for customers with an active Software Support Agreement. To obtain the patch users can send an email to email@example.com requesting the “Exele DCOM security 2021 patch”. Please include your current product license file.
The patch can be applied to the following Exele OPC products:
- TopView OPC/SCADA and OPC A&E version 6.25.3 and later
- OPCcalc versions 4.5 and 4.6
Earlier versions or TopView and OPCcalc will need to be upgraded to a version that supports the patch.
Read the full details of this change and impact on Exele OPC products
Citect OPC Server on Windows 7
This is a general support posting regarding TopView OPC communicating to Citect OPC Server on Windows 7. The two issues that a TopView user may experience are: TopView can connect to the OPC Server but reports that the server is not in a “running” ...
TopView OPC cannot connect as Service
This article is useful if TopView connects to your OPC server when run interactively, but cannot connect to remote OPC Server(s) when you run TopView as a Service. Interactive applications (non-Service) run under the account of the logged in ...
ClearSCADA connection fails with: "Error: CheckConnectionToServer > error creating group : AddGroup failed with error"
If you receive an error connecting to ClearSCADA with the following error message: ClearSCADA can be set up to use OPC private security and require credentials for permissions to connect to the server and retrieve tag values. To connect, provide the ...
TopView engine unable to connect to OPC UA server: SHA 1 Certificates are not trusted
Issue The TopView engine was unable to connect to the OPC UA server due to certificate issues. When inspecting the logs, we could see similar error messages to those that would occasionally appear when testing connections. This issue may show as the ...
Wonderware OPCENUM error 0x80040153
Note: the information below also exists as a PDF with screenshot images. Background If you install TopView OPC/SCADA on a Wonderware machine after installing the Wonderware OPC Server software, you may not be able to query to local OPC Servers ...